The Honeywell UDC Universal Digital Controller is a microprocessor-based stand alone controller. It combines the highest degree of functionality and. Find great deals for Honeywell UDC Universal Digital Controller. Shop with confidence on eBay!. There are UDC ‘s at both ends, however as the set point is managed by Lookout, the controllers just provide local control and display the.
|Published (Last):||11 December 2009|
|PDF File Size:||12.91 Mb|
|ePub File Size:||11.92 Mb|
|Price:||Free* [*Free Regsitration Required]|
Put the controller in manual and wind the output up and down while watching the measured value. This control occurs at two places on the reservoir: Uvc to the Modbus Community, about the world’s leading automation protocol.
By Darren on 15 November, – 4: The inlet control is likely configured for reverse operation increaed level decrease output, close gate.
Honeywell UDC3000 Specification
The bound manual you are looking for is Product E. Adjust the head gate position to maintain reservoir level. Username Password Remember me on this computer. Open the gate x amount for x period.
Honeywell UDC 3000 Universal Digital Controller
I would like a little more clarification on what your measuring and what your controlling – ‘gate position’ is pretty hard to measure unless you have some sort of valve positioner arrangement. The set point should be the desired level of the reservoir.
What I need to identify is the value that drives the output. The uec receives water from a river and releases it to the same down stream.
Your subscription request is being processed. The UDC configuration described is a level control wherein the object of the control loop appears to be:. By Patti on 4 November, – 2: You must be a Control. Some tips for better search results You have given some good problem definition. The output signal goes to the head gate and adjusts its position to increase or decrease flow into or out of the reservoir. Note that common words and, that, etc. ohneywell
Hi Patti The bound manual you are looking for is Product E. So that i can help you to resolve the problem. The ‘Rng1’ error your getting refers to the analogue input UDC’s are twin-loop controllers though in your application loop 2 is disabled It shows that error when the input range goes above 20ma or below 4ma.
By Steve Smoker on 4 October, – 7: By Chris Jenerick on 14 November, – Here are is the model number and settings.
HONEYWELL UDC SPECIFICATION Pdf Download.
It doesnt limit the controller output as the PID function will wind the output up until saturation if the measured value never reaches the setpoint. SPHiLim is the parameter that determines how high the setpoint on the controller can be wound up to. By Biscuithead on 12 July, – 7: Inlet Flow and Outlet Flow. Remember me on this computer. By Bill Clemons on 15 July, – 5: Try those and idc if its still not working. Perhaps you could order one from Honeywell.
The outlet control is likely configured for direct honeywe,l increased level increase output, open gate. Thanks for the reply.
To exclude a word, precede it with a “-“, as follows: Since the two can be connected through Lookout, you may consider implementing a staged control wherein the downstream UDC handles a majority of level changes in the reservoir small deviations in level. To search the site, enter your search terms in the box labeled honeywdll the site” and hit Enter. I’ve fiddled around with a few UDCs uxc being typical Honeywell the book is about as clear and thick as mud.
Use double quotes around phrases, as follows: